Which modules must be selected on the PROFINET side, if in PROFIBUS 1. universal modules and / or 2. consistency are projected?
When using universal modules, please note that they are only available on Profibus side. The picture of the DP / PN coupler web interface shows in red that in the 5 universal modules inthe first 3 slots no regular variables have been parameterized that are conform to the PN configuration. In this case, the SF LEDs on the DP/PNcoupler lights up and data transfer is not possible. The number of configured input or output bytes must match exactly with the other side.